What are construction site inspection requirements of diesel generator
1 , The construction site diesel generator rated voltage must be consistent with the external line power voltage level.
2 , Stationary diesel generating sets should be installed in an indoor meet the requirements on the basis of, and Interior floors higher 0.25~0.30m. Mobile diesel generating set should be in a horizontal position, place firm, the trailer should be a reliable ground, front and rear wheels stuck. Of diesel generator should built sheds for outdoor use.
3 , Diesel generators and control, distribution, repair room should be set to ensure electrical safety and meet the fire safety requirements. Exhaust pipe should extend outdoor and is prohibited in indoor and storing oil barrels near the exhaust pipe.
4 , Construction site installation of diesel-generator should be near load centers, and out of line, surrounding roads and avoiding pollution downwind side and easy ponding place.
5 , Generator power supply power supply chain must work with foreign lines, with no electric circuits in parallel operation. Dang 2 units and 2 or more generator parallel running, must be fitted with Synchronizer and synchronization in unit and then power to the load.